AIM Wall Cavity Fire Barrier & Fire Barrier Slab
Aim’s wall cavity fire barrier and fire barrier slab is a foil-faced rockwool stone fire and smoke barrier. It is suitable for all masonry cavity walls and curtain walls, for horizontal and vertical installation.
Furthermore, it can be installed in between a curtain wall system and a concrete floor slab.
It fills voids which are up to 400mm in size.
The different thicknesses it comes in are: 75mm and 100mm
Fire performance depends on the thickness of the fire barrier. Up to 2 hours fire protection available.
This product also provides sound insulation, reducing airborne sound transmission by at least 21dB Rw.
Tested to BS 476 part 20 and assessed by Warrington Fire Research Centre
Non-combustible to EN13501-1 and classified A1
Enhanced smoke resistance due to Class O reinforced aluminium foil facing
Manufacturing and dimensions:
No CFCs or HCFCs used in manufacturing – ozone depletion potential of zero.
- 75mm: 60 minutes – Butt end
- 100mm: 60 minutes Butt ends
- 100mm: 120 minutes
Slab size: 1000 x 600mm and 1000 x 1200mm (full pallets only)
Available polythene sleeved when supplied pre cut to size
The wall cavity barriers can be notched and in non standard lengths, if appropriate.
To install, simply push fit into place.
Ensure a tight fit is achieved, with 5% compression (approx.)
If air leakage also needs to be prevented, a seal must be achieved with taped joints and intumescent mastic to the linear edges to create a seal.
Clips are needed when installing this product to comply with the requirements of ADB (Approved Document B of the Building regulations in England).
PLEASE CONTACT US TO ENSURE YOU ARE USING THE CORRECT NUMBER OF CLIPS FOR YOUR VOID SIZE.
For horizontal installation, embed the clips to approximately 3/4 barrier width, prior to fitting the barrier. This will ensure that the top leg of the clip is level with the top of the barrier.
Push the barrier into the cavity until the top leg of the clips touches the floor slab and the top surface of the cavity barrier is flush with the slab.
For vertical installation, the clips may have to be fixed to the inner wall before the barrier is installed.
Barriers which must be installed before the outer wall layer may need retaining straps, which prevent them from falling off prior to the wall’s completion.
Butt end joints must be tight.
The ends of adjoining barriers must be fitted in contact for the full barrier width.
Please ensure that if the barrier is installed between two components which might separate in a fire, these components are mechanically linked to ensure separation does not occur.
Installation in Masonry Cavity Walls:
Horizontal Barrier: Bed the fixing clips into the joints in the internal leaf.
Install a damp proof membrane or a cavity tray immediately above, and to the outside of, the fire barrier.
For more information and to purchase, please contact our technical department on 01752 690997.
IMPORTANT INFORMATION ON PURCHASING OF PASSIVE FIRE PROTECTION PRODUCTS NOTICE:
The information displayed about the products on this website is to be used for guidance ONLY. We advise that all customers contact our technical department to obtain a free no obligation specification and quotation before purchasing goods directly from the website.
Please be aware that any negligence caused by failure to obtain the relevant advice, or availment of our specification and estimation service, will absolve International Passive Fire Ltd from any liability should Passive Fire Protection Products prepared, or used, by the purchaser, or any other parties, result in damage to property or human life, or for any monetary costs incurred due to incorrect usage.