Intumescent QWR Fire Collars by Quelfire
Quelfire’s Intumescent QWR Fire Collars are designed for plastic PVC, HDPE & PP pipes which penetrate through fire rated walls and floors.
They have been tested to achieve up to a 4 hour fire rating.
Available sizes are: 25mm, 32mm, 40mm, 50mm, 55mm, 63mm, 75mm, 82mm, 90mm, 110mm, 125mm, 160mm
The sizes in bold come in two different thicknesses. QWR55/CE/2, QWR110/CE/2 and QWR125/CE/2 have a lower fire rating than the standard QWR55/CE, QWR110/CE and QWR125/CE.
|Product Code||Pipe Size (mm)||Approx. space
needed around pipe
to fit QWR incl. fixing lugs (mm)
|QWR length (mm)||Fire Rating|
|QWR25/CE||25Ø||40||27Ø||50||Up to 4 Hours|
|QWR32/CE||32Ø||40||34Ø||50||Up to 4 Hours|
|QWR40/CE||40Ø||35||42Ø||50||Up to 4 Hours|
|QWR50/CE||50Ø||35||52Ø||50||Up to 4 Hours|
|QWR55/CE||55Ø||35||57Ø||50||Up to 4 Hours|
|QWR63/CE||63Ø||55||65Ø||50||Up to 4 Hours|
|QWR75/CE||75Ø||50||77Ø||50||Up to 4 Hours|
|QWR82/CE||82Ø||40||84Ø||50||Up to 4 Hours|
|QWR90/CE||90Ø||50||92Ø||50||Up to 4 Hours|
|QWR110/CE||110Ø||40||112Ø||50||Up to 4 Hours|
|QWR125/CE||125Ø||45||132Ø||50||Up to 4 Hours|
|QWR160/CE||160Ø||50||162Ø||50||Up to 4 Hours|
|QWR55/CE/2||55Ø||35||57Ø||50||Up to 2 Hours|
|QWR110/CE/2||110Ø||35||112Ø||50||Up to 2 Hours|
|QWR125/CE/2||125Ø||45||132Ø||50||Up to 2 Hours|
Why should I use Quelfire’s Intumescent QWR fire collars?
These pipe collars have been tested BSEN 1366-3: 2009 and classified according to EN 13501-2: 2007 + A1: 2009
They are CE marked.
Their fire testing shows they can provide up to a 4 hour fire rating. Weathering does not affect this performance. (Type X Durability)
Suitable for use on PVC, PVC-U, PE, HDPE, MDPE & PP pipes, on: concrete & masonry walls & floors and flexible walls – fire rated partition walls
They have also been tested on plasterboard ceilings/timber floors in accordance with the principles of BS EN1366-3:2009.
Their different sizes make them appropriate for 25-160mm pipes
You are able to retrofit them if needed.
Product Information and installation guidance
These pipe collars are made from a continuous pressed stainless steel flexible shell that contains a high performance graphite-based intumescent. This material reacts to heat, expands and chars, to plug the pipes.
Its built-in fixing lugs make it suitable for installing onto the structure.
There are different installation instructions for different pipework orientations.
In vertical orientations, fit one fire collar to the underside of the floor.
In horizontal orientations, install two pipe collars: one to each side of the wall.
Ensure the wall is clean and free from particles such as loose debris and dust.
Any irregularities between the collar and the wall or the pipe and the wall need to be filled with Quelstop Intumescent Acrylic Sealant.
Drill holes for the pipes as near to the outside diameter of the plastic pipes. Refer to the “performance” table above for more guidance.
If the holes are too large, contact us for guidance.
Feed the pipe collar around the pipe and pass the tongues one one side through their corresponding slots to secure the ends. Then bend the tongues back and use the correct fixings through all of the lugs to secure the collar fully into place.
If your require the installation instructions data sheet, please contact us.
For further installation information, please contact us.
Next day delivery available
peace of mind
14 day returns policy
Call for the best prices
Speak to our experts